In accordance with BS EN 13187:1999
Thermal Imaging Building Survey Requirements
The following are thermographic survey requirements in accordance with the recommendations of BS EN 13187:1999. As such, if any of the conditions above are not met before undertaking a thermographic survey, the conclusions and outcomes within our reports may not be fully accurate or actionable.
1. Temperature Difference
To ‘see’ heat loss (or gain) at least a 10°C temperature difference between the inside and outside must be achieved for a minimum of 24 hours prior to the survey if occupied, or 72 hours for a ‘dead’ building. If the building has no operational heating system, temporary direct heaters (such as space heaters) may be required.
2. Dry Surfaces
Prior to the start of a survey, building surfaces must be dry so that artificial cooling from moisture evaporation does not skew the results. For heavy building fabrics such as brick it’s highly recommended that the surface has been dry for at least 24 hours. For lightweight buildings, a minimum of 12 hours is recommended.
3. Full Access
Full access must be granted before any thermographic survey in order to analyse external elevations from inside of the thermal envelope. The building fabric must be kept free from obstructions such as furniture and building materials, as we cannot move anything during the survey and it takes at least an hour for the local temperature conditions to stabilise.
4. No Solar Radiation
5. Low Wind Speed
The wind speed during the survey should not be greater than 5m/s (18kph). This is in order to stop the cooling effect from exceeding recognised compensation values.
Sign Up To Our Newsletter!
Sign up to our newsletter and be the first to hear about our new training courses, new services and exclusive discounts available on the iRed Shop.